Centralised heat recovery unit with high-efficiency counterflow ENTHALPIC plate heat exchanger and powerful German fans (compact size)
Aerauliqa QR 350 E is a compact сentralised inflow-exhaust ventilation system with dimensions of 592x298x610 mm, the casing is made of galvanized steel with powder coating of white color RAL9010. The equipment is provided for use with an air duct system, which must transport air to all consumers. The equipment consists of a sound-insulating case made of EPP (foam polypropylene), two German EBM papst fans, a high-efficiency counterflow ENTHALPIC plate heat exchanger produced by the Dutch company Recair, G4 air purification filters (possible to install filter filters F7), an automatic summer bypass function (when outside air has a lower temperature than the indoor air, the air is supplied directly without passing through the heat exchanger, that makes it possible to cool the house in the summer period), the automation system to perform the following functions: 1 – day-off mode (the equipment is completely switched off), 2 - night mode (quieter operational mode), 3 - balance mode (change the ratio of inflow and exhaust air), 4 - weekly programmer function with a possibility of adjusting the hourly performance of the fans, 5 - indicator of filters contamination, 6 - different modes of connection to CO2 sensors or BMS system. Efficiency - 92%, volume of air - 333 m3 / hour.
|Contact Details||HeatRecovery, 21, Degtyarivska Str., Kyiv, 04119, Ukraine, tel.: +38 (044) 361-64-10, firstname.lastname@example.org|
|Manufacture Product Details||https://heatrecovery.com.ua/...|
|Efficiency in %||68.0|
Annual energy baseline 22,944kWh/a
Annual energy after replacement of Aerauliqa QR350E
Your annual savings
1. Inclusion of the technologies, equipment and materials in the Technology Selector is based solely on qualification under IQ energy’s ‘Minimum Energy Performance Standards’** and does not constitute an endorsement of the producers or suppliers of these products by the EBRD. Although every effort has been made to present correct and up to date data, EBRD does not accept responsibility for the accuracy of the data presented.
**Included technologies have been assessed to result in at least a 20% higher energy performance than the market average
2. The savings are calculated for the refurbishment of an average dwelling or the replacement of an average equipment in Ukraine. The actual savings of individual refurbishment projects/equipment can differ from the indicated savings due to specific climatic conditions, size of the dwelling/equipment, consumer behaviour, etc. The displayed energy efficiency measures only have an impact on individual household's bills (savings) if there is consumption based billing available.
3. Even though we have taken reasonable care to apply up-to-date energy prices when calculating savings in UAH, we do not take responsibility for the accuracy of any savings estimates stated on this Site.
4. All prices displayed in our Technology Selector are provided by the suppliers as indicative retail prices and should be used for reference purposes only. The actual prices of the vendors/retailors can be different from those on our web site due to various reasons beyond the influence of IQ energy programme. IQ energy programme does not bear any liability for the price information of any specific product. Please, check with suppliers actual prices for products and technologies you are interested in.